A durable, reusable can access valve designed specifically for use with Qwik System Flush®
Backseat valve in the closed position by turning knob of Can Access Valve fully counter clockwise. Twist Can Access Valve clockwise onto threaded tip of Qwik System Flush® as shown in photo #1
Attach hose to flare fitting on Can Access Valve as shown in photo #2.
Place the free end of the hose at the point of injection. If no flare fitting is available at the point of injection, either braze a flare fitting to the piping at the point of injection or use Line Set Flush Tool shown in photo #3(QT1110)
If you used a Line Set Flush Tool, place it in the line set at the point of injection as shown in photo #4.
Twist the knob of the Can Access Valve clockwise to release Qwik System Flush®, twist the knob counter clockwise to stop releasing Qwik System Flush® (Be sure that Qwik System Flush® aerosol can is held upside down during the flushing procedure as shown in photo #5).
Qwik System Flush® is used to flush contaminants such as debris, residual oil, acid, and moisture from refrigeration line sets. If you can't replace refrigeration line sets after a burnout or R-22 to R-410A change out, then you should use Qwik System Flush® to remove residual contamination. See our application bulletin for in depth instructions on how to use Qwik System Flush®.
5-10 times More Effective
Qwik System Flush® patented formulation is 5-10 times more effective in acid removal, moisture & oil absorption than competitive products. Qwik System Flush® is the ultimate solution for removing refrigerant line impurities during system change-out from R-22 to R410a or clean-up after a burnout. Qwik System Flush® is OEM Approved.